Falcor 9501 is a Nitrite-based corrosion and scale inhibitor, which has been formulated and specialized for closed-loop cooling systems.
Using Nitrite and similar compounds in its formula, Falcor 9501 can protect metals like Steel, Copper, Brass, and Iron from Cathodic and Anodic corrosion in system that use demineralized or soft water.
1 to 1.5 Kg/m3 of the chemical should be added to cycling water if Chloride content is less than 300 ppm (as NaCl). If greater than 300 ppm then 2 to 2.5 kg/m3 shall be used. The optimum dosage of the chemical will be recommended by Falizan Tasfyeh experts.
Falcor 9501 can be used both in concentrated
and diluted form. It is better to inject Falcor 9501 with dosing pump in
the suction line of circulating pump. Storage containers and applied devices
such as dosing pump and junction parts must be S.S.316 or 304 – PVC- PP- PE;
natural and synthetic rubber.
|Physical and Chemical properties|
|11 ± 0.5||PH (1%)|
|1.25 ± 0.05||Density in 20 °C|
|Completely Soluble||Water Solubility|
MATERIAL SAFETY DATA SHEET
- IDENTIFICATION OF THE PREPARATION AND OF THE COMPANY
Product Name: Falcor 9501
Application: Cooling Water Treatment
Manufacturer: Falizan Tasfyeh Co. Ltd
Head Office: Apt. #9; 5th Floor; Bldg. No. 164
Shahran Blvd., Tehran 14788-53483
Tel: +98 21 4430 4185 & 44353740
Fax: +98 21 44353950
Factory: Forj Alborz St., Km 25 of old Qazvin-Karaj road,
Telefax: +98 28 3293 8420 & 21
- COMPOSITION/INFORMATION ON INGREDIANTS
Sodium Nitrite- Mineral Alkaline Salts- Azole compounds- Acrylate Polymers- DM water
- POTENTIAL THREATS/ FIRST AID MEASURES
Remove to fresh air, rest, treat symptomatically. Obtain medical attention.
Remove contaminated clothing. Wash off affected area immediately with soap and plenty of water. If skin
irritation persists, obtain medical attention.
Immediately gently irrigate with clean water for at least 15 minutes. Move eyeball and keep eyelids wide open
and apart whilst irrigating. Obtain medical attention.
Rinse mouth immediately and repeatedly with water. Do not induce vomiting without medical advice.
Physical and Chemical Hazards:
Corrosive to Steel, copper and Alloys
- FIRE-FOGHTING MEASURES
The product is non-flammable
- ACCIDENTAL RELEASE MEASURES
Use safety dress, shoes, and face masks
Do not allow to enter sewers or water courses.
- HANDLING AND STORAGE
Be sure that first-aid kit is available; especially for eye cleaning. Prevent skin and eye contact
Keep indoor in a dry place. Prevent freezing the product
- EXPOSURE CONTROLS/PERSONAL PROTECTION
OCCUPATIONAL EXPOSURE LIMITS
General ventilation is recommended.
Respiratory protection not normally needed. If significant mists, vapors or aerosols are generated an approved respirator is recommended.
Standard protective clothing.
Chemical splash goggles.
Keep an eye wash fountain available. Keep a safety shower available. Wash hands at breaks and at the end of the shift. If clothing is contaminated, remove clothing and thoroughly wash the affected area. Launder contaminated clothing before reuse.
- SHELF LIFE:
24 months from production date